Wall-Hung Toilet Sink Shower
Vertical and horizontal discharges: 9 ft 100 ft
The Sanipack is a system that is used to install a complete bathroom up to 15 feet below the sewer line,
or even up to 150 feet away from a soil stack. It can handle the effluent from a toilet, sink and shower.
The Sanipack is simplicity itself to install; there are just four connections.
The macerator/pump is connected to the discharge pipe coming from a wall hung toilet
The toilet tank is connected to the water supply
The macerator/pump is connected to the small diameter discharge pipe work
The macerator/pump is connected to the electrical supply
The inside of the Sanipack is comprised of a pressure chamber, which starts and stops the unit,
and the motor, which drives the stainless steel macerator blades and the pump.
When the flush is activated, the water flowing into the Sanipack activates a micro switch
in the pressure chamber which in turn starts the motor.
The motor is sealed for life in an oil filled enclosure.
A common spindle/shaft drives the impeller and the macerator blades.
The moving parts therefore are kept to an absolute minimum.
Water and organic waste matter enter the chamber and are reduced to slurry as the macerator blades rotate at 3600 RPM.
The centrifugal force causes the reduced solids to be ejected through
a grill into the container where it is picked up by the impeller pump mounted beneath the motor.
The unit pumps the effluent upward to 15 feet and/or 150 feet horizontally (with gravity fall).
Once the water is discharged and the water level in the container goes down, the micro switch deactivates
the unit until the flush is activated again.
A normal operating cycle for Sanipack takes about 7-9 seconds depending upon the
discharge pipe run configuration; power consumption is therefore minimal.
In addition to the toilet waste, the Sanipack will also discharge gray water from
a variety of other sanitary fixtures such as: a sink, a shower and a urinal.
When adding a shower, a base will have to be constructed.
This base should be made out of a 2" x 6" (minimum) or 2” x 8” (recommended) on edge,
to allow for the installation of a P-trap and the required 1/4”per foot gravity flow towards the pump unit.
The wastewater from other sanitary fixtures is discharged into the Sanipack via
two 1-1/2 inch inlets on either side of the housing. Either one or both inlets can be used as required.
The discharge elbow on top of the Sanipack can be turned either to the left, to the right,
or towards the back, depending on the discharge installation. A non-return valve,
which comes already assembled on the discharge elbow, prevents back flow into the unit.
This unit has been designed with a vent connection on the lid. All plumbing codes require connection
to a vent system. Please note that the vent system should be a two-way air vent. The use of mechanical vents,
air admittance valves or similar devices are not permitted as these are considered one-way air vent systems.
It is also highly recommended for the macerator/pump to be connected to a Ground Fault Interrupter (GFI) circuit.
The Sanipack is designed to be used with a wall hung toilet. The depth of the case allows for this pump
to be installed within the wall. Since the reservoir, the macerating pump and the pipes are hidden from view,
this type of installation gives you the lean and clean look of a European bathroom.
Discharge Pipe Diameter (in) 3/4"
Vertical Discharge (ft) 9
Horizontal Discharge (ft) 100
Electrical Supply (V) 115
Motor Speed (RPM) 3600
Water Consumption (gallons) Depends on water closet
Discharge Rate at Max. Height (gpm) 13
Min. Gravity Fall on Horizontal Run 1/4" per foot
Dimensions (Height x Width x Depth) 11" x 16¾" x 4¾"
Maximum Temperature (°F) 104